Surge Protective Device Edco SHA Series Highway Lighting Protection Voltage Current Connection Mounting 120-480 VAC 30 Amp 10 AWG Wire Leads on Input & Output, 6 AWG Ground Flange *See Ordering Information for model number selection The Edco SHA Series provides surge protection for highway lighting/street pole applications. The suppressor is encapsulated in a weather resistant enclosure that can be installed inside the pole. The SHA Series is available in 120V, 240V, 277V and 480V Single Phase models. In addition, optional Low Capacitance (LC) and Both Black leads (BB) models are offered. General Technical Specifications Features SHA-1203 SHA-2403 SHA-2773 SHA-4803 Operating Voltage 120 VAC 240 VAC 277 VAC 480 VAC ■■ Proven Water Resistance Test Report Available Maximum Continuous Operating Voltage (MCOV) 150 VAC 275 VAC 320 VAC 550 VAC ■■ No Follow Current Model Voltage Configuration Continuous Operating Current ■■ Neutral-to-Ground Protection 30 A Operating Frequency 47-63 Hz Modes of Protection L-G, N-G Total Peak Surge Current Rating Clamp Voltage: @ 1ma (V peak) @ 200 amps Connection / Wire Type Current Drain Insulation to Ground Response Time Operating Temperature Dimensions (In/mm) Weight (lb/kg) ■■ Line-to-Ground Protection Single Phase 2W+G ■■ Solid State Design ■■ 5 Year Warranty 39 kA 240 V 430 V 510 V 910 V 395 V 710 V 850 V 1500 V Series Connected; Wire Leads 100 microamps > 600 Volts < 25 nanoseconds -40°C to +85°C 0.8” H x 2.875” W x 5.3” L [20.3 x 73.0 x 134.6 mm] 1 lb. [0.45 kg] Ordering Information MODEL APPLICATION SHA-1203 120 VAC, Single Phase, 2W+G SHA-2403 240 VAC, Single Phase, 2W+G SHA-2773 277 VAC, Single Phase, 2W+G SHA-4803 480 VAC, Single Phase, 2W+G SHA-4803BB SHA-_ _ _ _LC Both Leads Black Low Capacitance Option Installation Instructions V DANGER! Only qualified personnel should install or service this system. Electrical safety pre-cautions must be followed when installing or servicing this equipment. To prevent risk of electrical shock, turn off and lock out all power sources to the unit before making electrical connections or servicing. Seulement le personnel qualifié doit installer ou maintenir ce systéme. Des précautions de sécurité en électricité doivent être suivis lors de l’installation ou de la maintenance de cet equipement. Pour eviter tout risque de choc électrique, débranchez et verouiller toutes les sources d’alimentation de cet equipement avant de. 1. 2. 3. 4. 5. 6. 7. 8. Check voltage source to verify that the correct model Edco SHA Series is being installed. Disconnect power to light pole before beginning installation of surge protector. Remove hand hole panel on pole to gain access to the light wiring. Disconnect wire nuts connecting wire from electrical service to light. Check to ensure no voltage is present. Connect line side of Edco SHA Series to wire coming from service panel. L1 wire is connected to Line 1 (hot), L2 is connected to Line 2 or Neutral depending on the voltage. Connect the load side of the Edco SHA Series to wires going up to the light. L1 is connected to Line 1 (hot), L2 is connected to Line 2 or neutral depending on the voltage. Connect the Ground wire on the Edco SHA Series to the ground lug or screw inside the light pole. Carefully push the surge protector and wiring back inside the WH light pole and attach the hand hole panel on pole. GN Dimensions BK 1.17” [29.72] Typical 2.95” [74.93] Wiring BK LEAD LENGTH 1.5 [38 ” .1] 22” 1.17” [29.72] Typical GAUGE COLOR 6 AWG 9.0”Green [228.6] CONNECTION Ground 12” 10 AWG Black L-1 (Hot) 12” 10 AWG White L-2 (Neutral or Hot) Schematic 4.86” [123.44] L1 OUT Black Black L1 IN 5.25” [133.35] From Source 0.80” [20.3] Emerson Network Power Contact information Green White L2 IN SHA SERIES To Ballast L2 OUT White www.EmersonNetworkPower.com/Surge Surge Protection 100 Emerson Parkway Binghamton, NY 13905 T: (607) 721-8840 T: (800) 288-6169 F: (607) 722-8713 E: [email protected] IO-50145 5/15 Rev. 1 Printed in USA WH 2.9” [73.7] Emerson Network Power, the Emerson Network Power logo and Edco are trademarks and service marks of Emerson Electric Co. ©2014 Emerson Electric Co. While every precaution has been taken to ensure accuracy and completeness herein, Emerson Network Power Surge Protection assumes no responsibility, and disclaims all liability, for damages resulting from use of this information or for any errors or omissions. Specifications are subject to change without notice.