M-Series Time Delay Values NOTES: Delay Curves 12,14, 22, 24, 32, 34, 62, 64, 72, 74, 92, 94: Breakers to hold 100% and must trip at 135% of rated current and greater within the time limit shown in this curve. Delay Curves 10, 20, 30: Breakers to hold 100% and must trip at 150% of rated current and greater within the time limit shown in this curve. All Curves: Curve data shown represents breaker response at ambient temperature of 77°F (25°C) with no preloading. Breakers are mounted in standard wall-mount position. The minimum inrush pulse tolerance handling capability is 12 times the rated current on standard delays and 18 times the rated current on high inrush delays. These values are based on a 60 Hz 1/2 cycle, 8.33 ms pulse. High inrush delays should be specified for applications with high initial surge currents of short duration, such as switching power supplies, highly capacitive loads and transformer loads. Dual Rated AC/DC Instantaneous Short Medium www.carlingtech.com 11 A-D Series Time Delay Values PERCENT OF RATED CURRENT NOTES: UL489 C-Series Breakers available with Delay Curves 11, 12, 14, 16, 21, 22, 24, 26, 42, 44, 46. Delay Curves 11,12,14,16,21,22,24,26,42,44,46,52,54,56: Breakers to hold 100% and must trip at 125% of rated current and greater within the time limit shown in this curve. Delay Curves 32,34,36: Breakers to hold 100% and must trip at 135% of rated current and greater within the time limit shown in this curve. Delay Curves 10,20: Breakers to hold 100% and must trip at 150% of rated current and greater within the time limit shown in this curve. All Curves: Curve data shown represents breaker response at ambient temperature of 77°F (25°C) with no preloading. Breakers are mounted in standard wall-mount position. On 50 amp and less current ratings, the minimum inrush pulse tolerance handling capability is 12 times the rated current on standard delays and 25 times the rated current on high inrush delays. These values are based on a 60 Hz 1/2 cycle, 8.33 ms pulse. High inrush delays should be specified for applications with high initial surge currents of short duration such as switching power supplies, highly capacitive loads and transformer loads. AC DC Instantaneous Ultrashort Short 12 www.carlingtech.com A-D-Series Time Delay Values AC DC (A-D-Series Only) High Inrush AC High Inrush DC (A-D-Series Only) Medium Long Short Medium Long www.carlingtech.com 13 A-D-Series Time Delay Values AC/DC Short Medium Long 14 www.carlingtech.com E-Series Time Delay Values NOTES Delay Curves 10,20,30: Breakers to hold 100% and must trip at 150% of rated current and greater wthin the time limit shown in these curves. Delay Curves 12,14,16,22,24,26,62,64,66,72,74,76: Breakers to hold 100% and must trip at 125% of rated current and greater wthin the time limit shown in these curves. Delay Curves 32,34,36,92,94,96: Breakers to hold 100% and must trip at 135% of rated current and greater wthin the time limit shown in these curves. All curves: Data shown represents breaker response at ambient temperature of 77°F (25°C) with no preloading: Breakers are mounted in standard wall-mount position. The minimum inrush pulse tolerance handling capacity on the above standard delays is 16 times rated current &20 times rated current for high inrush delays based on a 60Hz 1/2 cycle, 8.33 ms pulse. AC DC Instantaneous Short Medium Long www.carlingtech.com 15 E-Series Time Delay Values AC/DC Instantaneous Short Medium Long 16 www.carlingtech.com F-Series TIme Delay Values NOTES: UL489 F-Series Breakers available with Delay Curves 11, 12, 14, 16. Delay Curves 11,12,14,16: Breakers to hold 100% and must trip at 125% of rated current and greater within the time limit shown in this curve. All Curves: Curve data shown represents breaker response at ambient temperature of 77°F (25°C) with no preloading. Breakers are mounted in standard wall-mount position. The minimum inrush pulse tolerance handling capabilities is 10 times rated current based on a 60 Hz 1/2 cycle, 8.33 ms pulse. DC Ultrashort Short Medium Long www.carlingtech.com 17

- Similar pages
- Time Delay Curves
- Telecom-Datacom Circuit Protection Selector Guide
- CX-Series Circuit Breaker
- Hydraulic Magnetic Circuit Breakers Selector Guide
- CX-Series Circuit Breaker
- Marine Switches,
- Renewable Energy Selector Guide
- CARLINGTECH CX2-S0-03-810-32A-0614
- G-Series Circuit Breaker News
- RENEWABLE ENERGY