CJ-series Controller Link Units CJ1W-CLK CSM_CJ1W-CLK_DS_E_6_3 New Controller Link Units, Now with 4,000 Send Words • The Controller Link is an FA network that can send and receive large amounts of data easily and at high speed. The Controller Link supports data links that enable sharing data between PLCs and computers and a message service that enables sending and receiving data whenever required. • Systems can be flexibly built by using Repeater Units to enable T-branches, long-distance wiring, and converting part of the network to optical cable. CJ1W-CLK23 Features • Large-capacity data links are easily achieved without programming simply by setting data link tables. • Up to 20,000 *1 send/receive words can be set per node for Units (up to 62,000 words for Boards). • Data links can be performed with up to 4,000 *2 words per node while ensuring data concurrency. • User-set data link tables can be changed while data links are operating. *3 • Errors for the entire system can be monitored by using error diagnosis support software and a variety of status flags. *1. Supported for unit version 1.2 or later. *2. CJ1W-CLK23 and 3G8F7-CLK@3 are supported. *3. Supported for CJ1W-CLK23, 3G8F7-CLK@3, and models ending with "-V1". System Configuration Wired Controller Link Units Basic Wiring (Daisy Chain Connection) A A A B A T-Branch Wiring, Partial Conversion to Optical Cable B A A (1) B 1km Max. * (1) Long-distance Wiring A D D A A (1) C (1) B A (2) A C D A (1) (1) 1km Max. * 1km Max. * 1km Max. * B (1) A: Wired Controller Link Unit B: Wired Controller Link Support Board C: Wire-to-Optical Repeater Unit D: Wire-to-Wire Repeater Unit * At 500 kbits/s (1): Twisted-pair cable (2): Optical cable 1 CJ1W-CLK Ordering Information International Standards • The standards are abbreviated as follows: U: UL, U1: UL (Class I Division 2 Products for Hazardous Locations), C: CSA, UC: cULus, UC1: cULus (Class I Division 2 Products for Hazardous Locations), CU: cUL, N: NK, L: Lloyd, and CE: EC Directives. • Contact your OMRON representative for further details and applicable conditions for these standards. Controller Link Units Specifications Unit classification Product name Communications cable Communications type Wired shielded twisted-pair cable * Data links and message service Duplex support Max. Units mountable per CPU Unit No. of unit numbers allocated Current consumption (A) Model 5 V DC Standards 24 V DC Controller Link Unit CJ1 CPU Bus Unit No 8 1 0.35 − CJ1W-CLK23 UC1,N,L, CE Note: This unit cannot be used with the Machine Automation Controller NJ-series. * Use the following special cable for shielded, twisted-pair cable. • ESVC0.5×2C-13262 (Bando Electric Wire: Japanese Company) • ESNC0.5×2C-99-087B (JMACS Japan Co., Ltd.: Japanese Company) • ESPC 1P×0.5mm2 (Nagaoka Electric Wire Co.,Ltd.: Japanese Company) • Li2Y-FCY2×0.56qmm (Kromberg & Schubert, Komtec Department: German Company) • 1×2×AWG-20PE+Tr.CUSN+PVC (Draka Cables Industrial: Spanish Company) • #9207 (Belden: US Company) Accessories There is no accessory for the CJ series Controller Link Unit. Controller Link Support Boards Specifications Product name Communications cable Communications type Controller Link Support Board for PCI Bus Wired shielded twisted-pair cable Data links and message service Accessories Model • CD-ROM ×1 * • INSTALLATION GUIDE (W467) ×1 3G8F7-CLK23-E • Communications connector ×1 Standards CE * The CD-ROM contains the following software. • Controller Link (PCI) Driver • FinsGateway Version 2003 (PCI-CLK Edition) • FinsGateway Version 3 (PCI-CLK Edition) • Setup Diagnostic Utility • C Library 2 CJ1W-CLK Repeater Units Name Specifications Controller Link Repeater Unit CS1W-RPT 01 PWR T/R1 T/R2 Model Wire-to-Wire Model CS1W-RPT01 Wire-to-Optical (H-PCF) Model *1 CS1W-RPT02 Wire-to-Optical (GI) Model *2 CS1W-RPT03 Standards UC1,CE SL1 TER SW SW1 1 BAUD 2 RATE ON TER SW SL2 DC24V INPUT Using Repeater Units enables T-branches and long-distance wiring for Wired Controller Link networks, 62-node configurations, and converting part of the network to optical cable. *1. When using wire-to-optical (H-PCF) cable, use a H-PCF cable (for both Controller Link and SYSMAC LINK) or a H-PCF optical fiber cable with connector. *2. When using wire-to-optical (GI) cable, use a GI optical cable (for Controller Link). Relay Terminal Block Name Specifications Model Standards Relay Terminal Block for Wired Controller Link Units Used for Wired Controller Link Units (set of 5) − CJ1W-TB101 Controller Link Units can be replaced without stopping the communications of the entire network if a Relay Terminal Block is installed in advance on the Unit in a Wired Controller Link network. Relay Terminal Blocks cannot be used on Controller Link Support Boards. H-PCF Cables and Optical Connectors Name Application/construction Specifications 1 2 3 4 Optical Fiber Cables Optical Connectors (Crimp-cut) Controller Link, SYSMAC LINK, SYSBUS 5 6 1. Optical fiber single-core cord 2. Tension member (plastic-sheathed wire) 3. Filler (plastic) 4. Filler surrounding signal wires (plastic, yarn, or fiber) 5. Holding tape (plastic) 6. Heat-resistant PV sheath Two-core optical cable with tension member Model Black 10 m S3200-HCCB101 Black 50 m S3200-HCCB501 Black 100 m S3200-HCCB102 Black 500 m S3200-HCCB502 Black 1000 m S3200-HCCB103 Orange 10 m S3200-HCCO101 Orange 50 m S3200-HCCO501 Orange 100 m S3200-HCCO102 Orange 500 m S3200-HCCO502 Orange 1000 m S3200-HCCO103 Half lock S3200-COCF2571 Full lock S3200-COCF2071 Standards − CS1W-RPT02 H-PCF Optical Fiber Cables with Connectors (Black Composite Cables with Two-Optical Lines and Two Power Supply Lines) Application Appearance Model Standards S3200-CN@@@-20-20 Controller Link, SYSMAC LINK S3200-CN@@@-20-25 − S3200-CN@@@-25-25 Optical connectors for H-PCF Optical Cables with Connectors are adhesive polished. • Cable Length The following cable lengths are available: 2 m, 5 m, 15 m, 20 m. For lengths of 21 m or more, contact your OMRON sales representative. 3 CJ1W-CLK • Model Numbers (1) 2 m, 5 m, 10 m, 15 m, or 20 m (2) 21 m or longer S3200-CN@@@ @@@-20-25 1. 2. 1. H-PCF Optical Fiber Cable S3200-CN-20-20 1. 3. 2. Cable length @@@ Length 201 2m 501 5m 102 10 m 152 15 m 202 20 m 3. Specify the cable length in meters. 3. Connectors (both ends) Number Connector lock 20 Full-lock 25 Half-lock Cable length • Optical Connector Assembly Tool Name Applicable Unit Model This tool is used on site for mounting crimp-cut connectors and hard plastic-clad silica optical fiber for optical transmission systems of C-series SYSBUS, SYSMAC LINK, and Controller Link. Optical Fiber Assembly Tool * Manufacturer Standards Sumitomo Electric Industries, Ltd. CAK-0057 − * There is a risk of quality problems when using cables assembled by typical users, so we recommend purchasing cables with preattached connectors or having a qualified technician assemble the cables. GI Optical Cables A qualified technician must select, assemble, and install GI Optical Fiber Cable, so always let an optical cable specialist handle the GI cable. Usable Optical Cables and Optical Connectors • Optical fiber types: Graded, indexed, multi-mode, all quartz glass, fiber (GI-type AGF cable) • Optical fiber construction (core diameter/clad diameter): 62.5/125 μm or 50/125 μm • Optical fiber optical characteristics of optical fiber: Refer to the tables. • Optical connector: ST connector (IEC-874-10) • 50/125 μm AGF Cable Item Minimum Numerical Aperture (N.A) − Transmission loss (dB) − Connection loss (dB) Transmission bandwidth (MHz-km) − 500 • 62.5/125 μm AGF Cable Standard Maximum − − Item Minimum − Numerical Aperture (N.A) − Transmission loss (dB) − − 0.21 − Conditions 3.0Lf 0.5 km ≤ Lf 3.0Lf+0.2 0.2 km ≤ Lf ≤ 0.5 km 3.0Lf+0.4 Lf ≤ 0.2 km 1.0 − λ = 0.8 μm Ta = 25°C λ = 0.8 μm, one location Connection loss (dB) λ = 0.85 μm (LD) Transmission bandwidth (MHz-km) Lf is fiber length in km, Ta is ambient temperature, and λ is the peak wavelength of the test light source. − 200 Standard Maximum Conditions − − 0.28 − − − 3.5Lf 0.5 km ≤ Lf 3.5Lf+0.2 0.2 km ≤ Lf ≤ 0.5 km 3.5Lf+0.4 Lf ≤ 0.2 km 1.0 λ = 0.8 μm, one location − λ = 0.8 μm Ta = 25°C λ = 0.85 μm (LD) Lf is fiber length in km, Ta is ambient temperature, and λ is the peak wavelength of the test light source. 4 CJ1W-CLK Mountable Racks NJ system Model CPU Rack CJ1W-CLK23 Unit version 2.0 CJ1W-CLK21-V1 *1 Unit version 1.2 *1. *2. *3. *4. Expansion Rack Not supported CJ1 system CPU Rack Expansion Backplane 8 Units (per CPU Unit) CP1H system NSJ system CP1H PLC NSJ Controller Expansion Backplane 2 Units *2 Not supported *3 8 Units *4 Discontinuation models in July 2012. A CP1W-EXT01 CJ Unit Adaptor is required. One NSJW-CLK21-V1 can be mounted to the NSJ Controller. If an Expansion Rack is used, the NSJW-CLK21-V1 cannot be mounted to the NSJ Controller. Communications Specifications Items Specifications Model CJ1W-CLK23 3G8F7-CLK23-E CJ1W-CLK21-V1 *1 3G8F7-CLK21-EV1 *1 Type Wired (shielded twisted-pair cable) Communications method N:N token-bus method Code Manchester code Modulation Baseband code Synchronization Flag synchronization (conforms to HDLC frames) Transmission path format Multidrop method (bus type) Transmission speed Maximum transmission distance The following are the maximum transmission distances depending on the transmission speed. 2 Mbits/s: 500 m 1 Mbits/s: 800 m 500 kbits/s: 1 km Maximum distance between nodes Not specified. (Maximum transmission distance must be satisfied for the entire system.) Medium Specified shielded twist-pair cable Two signal wires, one shield Node connection method PLC: Connection to terminal block Computer: Connection using special (supplied) connector Maximum number of nodes 32 or 62 nodes *2 *3 Applicable Programming Devices CX-Integrator in CX-One, CX-Net in CX-Programmer *3, and Programming Console Communications functions Data links and message service Number of data link words Send words per node: 4,000 words max. (CJ1W-CLK@3), 1,000 words max. (All other Units) Number of send/receive words per node: 12,000 words max. (Pre-Ver. 1.2) 20,000 words max. (unit Ver. 1.2 or later) Total number of send words per network: 62,000 words max. Data link areas PLC: Bit areas (CIO Area, Work Area, Link Area *4), Data Memory (DM), Extended DM Area (EM) Computer: FinsGateway event memory Message length 2,012 bytes max. (including the header) RAS functions Error control • • • • • Polling node backup function Self-diagnosis function (hardware checking at startup) Echoback test and broadcast test (using the FINS command) Watchdog timer Error log function Manchester code check CRC check (CCITT X16+X12+X5+1) *1. Discontinuation models in July 2012. *2. With wired models, the maximum number of nodes is 32 if Repeater Units are not used. A Repeater Unit is required when building a network with more than 32 nodes. If a Repeater Unit is used, be sure to use only the following Controller Link Units or Boards and set the Wired Network 62 Node Enable Bit in the DM Parameter Area software switches at all nodes. CS1W-CLK23/CLK21-V1 CJ1W-CLK23/CLK21-V1 3G8F7-CLK23-E/CLK21-EV1 *3. CX-Net in CX-Programmer version 3.1 or earlier can be used only in a system with a maximum of 32 nodes (node address 1 to 32). If a system is to be used with a maximum of 62 nodes (node addresses 1 to 62), use CX-Net in CX-Programmer version 3.2 or higher or the CX-Integrator. *4. CJ-series PLCs do not have a Link Area, but LR000 to LR199 are automatically converted CIO 1000 to CIO 1199. 5 CJ1W-CLK Individual Specifications Controller Link Units Item Model Applicable PLC Number of mountable Units Installation site Storage location of network parameters and manually set data link tables Storage location of routing tables Weight Current consumption: 5 V in PLC * Discontinuation models in July 2012. Specifications CJ1W-CLK23 CJ1W-CLK21-V1 * All CJ-series CPU Units 8 max. Install onto a CPU Backplane or Expansion Backplane (classified as a CPU Bus Unit). System Bus Unit Area (in the CPU Unit parameter area). CPU Unit parameter area 110 g 0.35 A Controller Link Support Boards (for PCI Bus), New Models Item Specifications 3G8F7-CLK23-E 3G8F7-CLK13-E 3G8F7-CLK53-E IBM PC/AT or compatible • CPU: Intel Celeron 400 MHz or better • Main memory: 128 MB minimum • One or more PCI bus slots (PCI bus revision 2.0 or later, power supply: 5 V) Computer-compatible models • Free hard disk space: 70 MB min. • CD-ROM drive: One required for installation • Display: VGA (640 x 480 (pixels) min.) (Other conditions conform to the OS.) • FinsGateway Version2003 *1 Windows 7 (32bit) Professional Windows 7 (32bit) Home Premium Windows Vista Business Windows Vista Home Premium Windows XP Professional Windows XP Home Edition Compatible OS Windows 2000 Professional • FinsGateway Version3 *2 Windows XP Professional Windows XP Home Edition Windows 2000 Professional Windows NT4.0 (Service Pack 3 or higher) Windows ME Windows 98SE 120 g 124 g Weight 104 g (excluding mounting bracket) (excluding mounting bracket) 5 V in PLC 0.35 A 0.54 A 0.60 A Current consumption External 24 V − 0.35 A 0.35 A *1. Install the software from CD Ver. 3.10 or higher if the operating system is Windows 7 (32bit) or Windows Vista. *2. Install FinsGateway version 3 if the operating system is Windows NT 4.0 (Service pack 3 or higher), Windows ME, or Windows 98SE. In that case, however, the new functions of Controller Link Support Boards for the PCI Bus cannot be used (i.e., automatic data link creation with 1:N allocation, changing data link tables with active data links, 62-node setting for wired models, and maximum of 4000 send words). Model Controller Link Support Boards (for PCI Bus), Old Models Item Model *1 Computer-compatible models Compatible OS *2 Weight Specifications 3G8F7-CLK21-EV1 3G8F7-CLK12-EV1 3G8F7-CLK52-EV1 IBM PC/AT or compatible • CPU: Intel Celeron 400 MHz or better • Main memory: 128 MB minimum • One or more PCI bus slots (PCI bus revision 2.0 or later, power supply: 5 V) • Free hard disk space: 70 MB min. • CD-ROM drive: One required for installation • Display: VGA (640 x 480 (pixels) min.) (Other conditions conform to the OS.) • FinsGateway Version2003 Windows XP Professional Windows XP Home Edition Windows 2000 Professional • FinsGateway Version3 Windows XP Professional Windows XP Home Edition Windows 2000 Professional Windows NT4.0 (Service Pack 3 or higher) Windows ME Windows 98SE 120 g 124 g 104 g (excluding mounting bracket) (excluding mounting bracket) 0.35 A 0.54 A 0.60 A − 0.35 A 0.35 A 5 V in PLC External 24 V *1. Discontinuation models in July 2012. *2. Install FinsGateway version 3 if the operating system is Windows NT 4.0 (Service pack 3 or higher), Windows ME, or Windows 98SE. In that case, however, the new functions of Controller Link Support Boards for the PCI Bus cannot be used (i.e., automatic data link creation with 1:N allocation, changing data link tables with active data links, 62-node setting for wired models, and maximum of 4000 send words). Current consumption 6 CJ1W-CLK Repeater Units Item Model Supported Units/Boards Transmission line Transmission line format Installation Weight Allowable power supply voltage range Current consumption Inrush current Specifications CS1W-RPT01 CS1W-RPT02 CS1W-RPT03 All wired Controller Link Units and Boards Note: If a maximum of 62 nodes is used, models that support 62 nodes must be used. Wire-to-wire Wire-to-optical (H-PCF) Wire-to-optical (GI) Multi-drop 1:1 type 1:1 type Tree Repeater Units are not mounted to the PLC. They are mounted separately with screws or on a DIN Track. 126 g 113 g (excluding mounting bracket) 116 g (excluding mounting bracket) 20.4 to 26.4 V DC (24 V DC −15 to 10%) 24 V DC at 0.06 A 2.5 A max. at 24 V DC (5 ms after startup) 24 V DC at 0.07 A Repeater Units are used to expand the Controller Link network for wired models. For Wired-to-optical Repeater Units, always use a set of two (1:1). Optical Ring Controller Link Units and Boards cannot be connected to the optical cable section between Repeater Units. External Interface CJ1W-CLK23/CJ1W-CLK21-V1 * CLK21-V1 RUN ERC INS SD TER ERH M/A LNK RD EF012 6789 345 ABCD 901 456 23 LED Indicators Display the Unit and network status. UNIT No. Unit Number Switch One rotary switch. The unit number of the Unit on the PLC is set in single-digit hexadecimal. NODE No. x101 Node Address Switches Two rotary switches. The node address of the Unit on the Controller Link Network is set in 2-digit decimal. 78 901 78 ON 1 2 ON 0 x10 1 BAUD 2 RATE ON SW1 456 23 Baud Rate Switches A two-pin DIP switch. The following setting is made. Pins 1 and 2: Baud rate TER SW BD H Terminating Resistance Switch A slide switch. Use this switch to set the terminating resistance to ON for nodes at both ends of the Controller Link Network. BD L SHLD Terminal Block for the Communications Cable Terminals to connect to the Controller Link Network communications cable (twisted-pair cable). * Discontinuation models in July 2012. Definition of Terminal Block Pin Names for Communications Cables Marking Notation Signal name Line color ■ BD H Communication data, high Black @ BD L Communication data, low White None SHLD Shield None Crimp Terminals Use crimp terminals (M3) having the dimensions shown below. 6.2 mm max. 6.2 mm max. 7 CJ1W-CLK Differences in Specifications of New and Old Models Controller Link Units Functions CJ1W-CLK23 CJ1W-CLK21-V1 The following models are discontinued. CJ1W-CLK21-V1 The following models are discontinued. CJ1W-CLK21 The following models are discontinued. Unit version 2.0 Unit version 1.2 Pre-Ver. 1.2 Pre-Ver. 1.2 Number of data link send words (data link areas that are created for a single node in a single PLC) 20,000 max. Number of send words per node (total of area 1 and area 2) 4,000 words max. (user-set links only) Data Link Area Allocation setting can be performed for same areas in Allocation setting can be performed for same areas in areas 1 and 2. areas 1 and 2. 12,000 max. 1,000 words max. Max. Units mountable per PLC 8 Units Automatic data link setting 4 Units Supported for equality layout only. Choose from equality layout or 1:N allocations (common type, 1:1, chain type) Changing data link allocations Supported (Data link tables can be changed during active data links.) during active data links Not supported. Maximum connectable nodes 62 nodes *1 32 nodes Mixed use Yes *2 Compatible support software CX-Integrator for CX-One CX-Net for V2.1or higher, or CX-Net CX-Programmer Ver. 5.0 for CX-Programmer Ver. or higher 7.2 or higher CX-Net for CX-Programmer Ver. 3.2 or higher CX-Net for CX-Programmer Ver. 1.0 or higher *1. For wired models, the maximum number of nodes is 32 if Repeater Units are not used. *2. Old models and new models can be used mixed on the same network. In that case, however, build the system using the specifications for the old models. The data link send/receive words can be separately set to their maximums when new and old models are mixed. Controller Link Support Boards (for PCI Bus) Functions 3G8F7-CLK23-E Number of data link send/ receive words (data link areas for sending/receiving that are created for a single node in a single computer) 62,000 max. Send words per node 4,000 words max. (user-set links only) 3G8F7-CLK21-EV1 The following models are discontinued. 3G8F7-CLK21-E The following models are discontinued. 32,000 max. 1,000 words max. Changing data link allocations Supported. (Data link tables can be changed during active data links.) during active data links Not supported. Maximum connectable nodes 62 nodes *1 32 nodes Mixed use Yes *2 Compatible FinsGateway *3 FinsGateway Version 2003.21 or higher (In CD Ver. 3.00 or higher) FinsGateway Version 2003.00 or higher (In CD Ver. 2.00 or higher) FinsGateway Version 3.00 or higher (In CD Ver. 1.00 or higher) Compatible support software CX-Integrator for CX-One Ver. 2.1 or higher , or CX-Net for CX-Programmer Ver. 7.2 or higher CX-Net for CX-Programmer Ver. 3.2 or higher CX-Net for Ver. 1.0 or higher *1. For wired models, the maximum number of nodes is 32 if repeater units are not used. *2. Old models and new models can be used mixed on the same network. In that case, however, build the system using the specifications for the old models. The data link send/receive words can be separately set to their maximums when new and old models are mixed. *3. FinsGateway Version 2003 is compatible with Windows 7 (32bit) (CD Ver.3.10 or higher), Windows Vista (CD Ver.3.10 or higher), Windows XP and Windows 2000. For Windows NT4.0 (Service Pack 3 or higher), Windows ME, or Windows 98SE, use FinsGateway Version3. (With FinsGateway Version 3, only functions supported by the 3G8F7-CLK21 can be used.) 8 CJ1W-CLK Usage Precautions • Old models and new models can be used mixed on the same network. In that case, however, build the system using the specifications for the old models. The data link send/receive words can be separately set to their maximums when new and old models are mixed. • Repeater Units can be used to expand a Wired Controller Link Network. For Wired-to-optical Repeater Units, always use a set of two (1:1). Optical Ring Controller Link Units and Boards cannot be connected to the optical cable section between Repeater Units. • Connect Repeater Units so that there are no more than two stages between any two nodes. One set of two Wire-to-Optical Repeater Units is counted as one stage. Dimensions (Unit: mm) CJ1W- CLK23/ CJ1W- CLK21-V1 * 65 2.7 90 2.7 82 31 * Discontinuation models in July 2012. 9 CJ1W-CLK Related Manuals Cat.No Model Name Applications Description W309 CS1W-CLK23 CS1W-CLK21-V1 CJ1W-CLK23 CJ1W-CLK21-V1 C200HW-CLK21 CVM1-CLK21 CQM1H-CLK21 CS1W-RPT01/02/03 Controller Link Units Operation Manual W422 3G8F7-CLK12-V1 3G8F7-CLK52-V1 3G8F7-CLK21-V1 Used when information Controller Link Support Boards for PCI Bus regarding setup procedures Describes the setup method for Installation Guide for Controller Link Support the Controller Link Support Boards (3G8F7-CLK12/21/52-V1) Boards for PCI bus for PCI bus connections. connections is needed. W467 3G8F7-CLK13 3G8F7-CLK12-V1 3G8F7-CLK53 3G8F7-CLK52-V1 3G8F7-CLK23 3G8F7-CLK21-V1 Used when information Controller Link Support Board for PCI Bus regarding setup procedures Describes the setup method for Installation Guide for Controller Link Support the Controller Link Support Boards (3G8F7-CLK13/12-V1/53/52-V1/23/21-V1) Boards for PCI bus for PCI bus connections. connections is needed. W383 3G8F7-CLK13 3G8F7-CLK12-V1 3G8F7-CLK53 3G8F7-CLK52-V1 3G8F7-CLK23 3G8F7-CLK21-V1 Used when information regarding setup procedures Describes the setup method for Controller Link Support Boards for PCI Bus for Controller Link Support the Controller Link Support Boards Operation Manual Boards for PCI bus for PCI bus connections. connections is needed. W464 CXONE-AL@@D-V@ CX-Integrator Operation Manual Used when network setup or network monitoring needs to be performed. Describes the operating procedures for the CX-Integrator. CXONE-AL@@D-V@ CX-One FA Integrated Tool Package Setup Manual Used when installing software from the CX-One. Provides an overview of the FA Integration Tool Package CX-One, and describes the CX-One installation procedures. W463 Used when information regarding operating procedures for Wired Controller Link Units is needed. Describes operating procedures for Controller Link Units. Controller Link Units can connect to Wired Controller Link Units. 10 Terms and Conditions Agreement Read and understand this catalog. Please read and understand this catalog before purchasing the products. Please consult your OMRON representative if you have any questions or comments. Warranties. (a) Exclusive Warranty. Omron’s exclusive warranty is that the Products will be free from defects in materials and workmanship for a period of twelve months from the date of sale by Omron (or such other period expressed in writing by Omron). Omron disclaims all other warranties, express or implied. (b) Limitations. OMRON MAKES NO WARRANTY OR REPRESENTATION, EXPRESS OR IMPLIED, ABOUT NON-INFRINGEMENT, MERCHANTABILITY OR FITNESS FOR A PARTICULAR PURPOSE OF THE PRODUCTS. BUYER ACKNOWLEDGES THAT IT ALONE HAS DETERMINED THAT THE PRODUCTS WILL SUITABLY MEET THE REQUIREMENTS OF THEIR INTENDED USE. Omron further disclaims all warranties and responsibility of any type for claims or expenses based on infringement by the Products or otherwise of any intellectual property right. (c) Buyer Remedy. Omron’s sole obligation hereunder shall be, at Omron’s election, to (i) replace (in the form originally shipped with Buyer responsible for labor charges for removal or replacement thereof) the non-complying Product, (ii) repair the non-complying Product, or (iii) repay or credit Buyer an amount equal to the purchase price of the non-complying Product; provided that in no event shall Omron be responsible for warranty, repair, indemnity or any other claims or expenses regarding the Products unless Omron’s analysis confirms that the Products were properly handled, stored, installed and maintained and not subject to contamination, abuse, misuse or inappropriate modification. Return of any Products by Buyer must be approved in writing by Omron before shipment. Omron Companies shall not be liable for the suitability or unsuitability or the results from the use of Products in combination with any electrical or electronic components, circuits, system assemblies or any other materials or substances or environments. Any advice, recommendations or information given orally or in writing, are not to be construed as an amendment or addition to the above warranty. See http://www.omron.com/global/ or contact your Omron representative for published information. Limitation on Liability; Etc. OMRON COMPANIES SHALL NOT BE LIABLE FOR SPECIAL, INDIRECT, INCIDENTAL, OR CONSEQUENTIAL DAMAGES, LOSS OF PROFITS OR PRODUCTION OR COMMERCIAL LOSS IN ANY WAY CONNECTED WITH THE PRODUCTS, WHETHER SUCH CLAIM IS BASED IN CONTRACT, WARRANTY, NEGLIGENCE OR STRICT LIABILITY. Further, in no event shall liability of Omron Companies exceed the individual price of the Product on which liability is asserted. Suitability of Use. Omron Companies shall not be responsible for conformity with any standards, codes or regulations which apply to the combination of the Product in the Buyer’s application or use of the Product. At Buyer’s request, Omron will provide applicable third party certification documents identifying ratings and limitations of use which apply to the Product. This information by itself is not sufficient for a complete determination of the suitability of the Product in combination with the end product, machine, system, or other application or use. Buyer shall be solely responsible for determining appropriateness of the particular Product with respect to Buyer’s application, product or system. Buyer shall take application responsibility in all cases. NEVER USE THE PRODUCT FOR AN APPLICATION INVOLVING SERIOUS RISK TO LIFE OR PROPERTY OR IN LARGE QUANTITIES WITHOUT ENSURING THAT THE SYSTEM AS A WHOLE HAS BEEN DESIGNED TO ADDRESS THE RISKS, AND THAT THE OMRON PRODUCT(S) IS PROPERLY RATED AND INSTALLED FOR THE INTENDED USE WITHIN THE OVERALL EQUIPMENT OR SYSTEM. Programmable Products. Omron Companies shall not be responsible for the user’s programming of a programmable Product, or any consequence thereof. Performance Data. Data presented in Omron Company websites, catalogs and other materials is provided as a guide for the user in determining suitability and does not constitute a warranty. It may represent the result of Omron’s test conditions, and the user must correlate it to actual application requirements. Actual performance is subject to the Omron’s Warranty and Limitations of Liability. Change in Specifications. Product specifications and accessories may be changed at any time based on improvements and other reasons. It is our practice to change part numbers when published ratings or features are changed, or when significant construction changes are made. However, some specifications of the Product may be changed without any notice. When in doubt, special part numbers may be assigned to fix or establish key specifications for your application. Please consult with your Omron’s representative at any time to confirm actual specifications of purchased Product. Errors and Omissions. Information presented by Omron Companies has been checked and is believed to be accurate; however, no responsibility is assumed for clerical, typographical or proofreading errors or omissions. 2016.4 In the interest of product improvement, specifications are subject to change without notice. OMRON Corporation Industrial Automation Company http://www.ia.omron.com/ (c)Copyright OMRON Corporation 2016 All Right Reserved.