SLATE ™ Base Module R8001A1001 INSTALLATION INSTRUCTIONS Scan for more information Application SLATE™ brings configurable safety and programmable logic together into one single platform. The platform can easily be customized for almost any requirement or application—offering virtually limitless development opportunities with far less complexity. The R8001A1001 base module provides communications and power supply for the SLATE system, configurable safety for Burner Control, Flame Amps, Fuel Air Ratio, and Limit modules, and programmable logic for Digital and Analog I/O, and Annunciation. SLATE is a combustion system with configurable safety and programmable logic. The system is modular in format and DIN rail mountable. Modules include: • Base • Burner Control Module • Flame Amp Modules • Fuel Air Ratio Control Module • Limit Module • Analog I/O Module • Digital I/O Module • Annunciator Module SLATE™ BASE MODULE R8001A1001 3 Features Within the SLATE system, the base module provides: • Power to all modules with multiple voltage options • External communication protocols Modbus/TCP, BACnet MSTP or IP, and web services • Overall health of the system • The ability to do remote troubleshooting • Network identification of the system as a single device • Web-based pages (both Honeywell provided and designer customized) for Web browser access to the system • Module identification for the system • Event log storage for user lockouts, fault history, and user requested events • Trend logging for user specified data Specifications Electrical Ratings: Input Voltage and Frequency: 24 VDC (± 15%), 24 VAC (± 15%), 50/60 Hz, 85-264 VAC, 50/60 Hz Output Voltage: 18 VDC (± 1 VDC) Power Dissipation: 38W max @ 24V (approx. 12 modules), 45W max @ 85-264V (approx. 14 modules) Fusing Total Connected Modules: 5A, slow type, non-replaceable Terminal Ratings: See Table 1. Terminal Description Rating E100-1 L1 - line voltage hot --- E100-2 L2 - line voltage common --- E100-3 PE - Earth Ground --- 432-00005—01 a Terminal Description Rating E200-1 Alarm (dry contacts) 120 / 240 VAC, 1A pilot duty E200-2 Alarm (dry contacts) 120 / 240 VAC, 1A pilot duty E200-3 Unused --- E200-4 A (BACnet MS/TP) --- E200-5 B (BACnet MS/TP) --- E200-6 GND (BACnet MS/TP) --- E200-7 VAUX + 3.3-24 VDC output, 250mA max E200-8 VAUX - a 3.3-24 VDC output, 250mA max Do not connect to earth ground. Table 1. Terminal Ratings. Environmental Ratings Ambient Temperature: Operating: -20°F to +150°F (-29°C to +66°C). LCD Operating: 32°F to +150°F (0°C to +66°C). Shipping: -40°F to +150°F (-40°C to +66°C) Humidity: 95% continuous, noncondensing. Vibration: 0.5G environment Dimensions:See Fig. 1 Weight: 2 lb 1 oz (0.94 Kg) Approvals: Underwriters Laboratories Inc. Listed, File: MP268. IRI acceptable. Federal Communications Commission: Part 15, Class A Emissions. Must be mounted inside a grounded metal enclosure. Mounting:DIN Rail (See Fig. 4) SLATE™ BASE MODULE R8001A1001 5 7-3/32 (180) 6-3/32 (155) 5-19/64 (135) M35389 Fig. 1. Dimensions in in. (mm). 632-00005—01 Principal Technical Features The R8001A1001 base module provides communications and power supply for the SLATE system, configurable safety for Burner Control, Flame Amps, Fuel Air Ratio, and Limit modules, and programmable logic for Digital and Analog I/O, and Annunciation. Communications The base module provides communications via Modbus IP RS485, BACNet IP/MSTP (RS-485), and Web Services. User Interface The menu-driven user interface provides system status and alerts via a dot matrix display on the front of the module. It is controlled by a 7-button keypad. LED Array There are three LEDs on the front of the base module that provide quick identification of system status and problems. This status is broadcast to other modules on the platform bus in case they are affected by the inoperable module(s). LED Color Power No light Green CPU Fault Description System does not have power System has power Red No wire sheet or problem with the wire sheet Green Running Red Fault No light Running Table 2. LED Descriptions. SLATE™ BASE MODULE R8001A1001 7 LCD Screen The base module LCD screen will show information about various modules and other parts of the combustion system. Use the arrow keys to navigate the items on the LCD screen, then press OK to select one. In Fig. 2, Burner6 is in Lockout. For additional information, navigate to that menu item and press OK. Light Sensor > > Slate _____________________________ _ _ _ Application: Running _ _ _ _ m6 Burner6: Lockout >_ _ 1FM-VU-Achk Running m1 Base: Running m2 Burner: Hold > _____________________________ scroll 8:07 am OK:select Power CPU Fault Status Main Power OK Menu M35422 Fig. 2. LCD display showing a fault (Burner6 is in Lockout). Additional information, as shown in Fig. 3, is displayed. Use this information to troubleshoot the combustion system. 832-00005—01 < m6 Burner6: FAULT _____________________________ Fault code: 35 Flame is OFF Date: 4 Nov 2014 Time: 3:30 PM Power CPU Fault Light Sensor > > _____________________________ scroll <back Status Main Power OK Menu M35423 Fig. 3. Additional lockout information. Light Sensor SLATE contains a light sensor that is used when the system is exposed to light. This is a power saving feature. Installation WARNING Fire or Explosion Hazard Can cause severe injury, death, or property damage. Verification of safety requirements must be performed each time a control is installed on a burner to prevent possible hazardous burner operation. SLATE™ BASE MODULE R8001A1001 9 When Installing This Product 1. Read these instructions carefully. Failure to follow them could damage the product or cause a hazardous condition. 2. Check the ratings given in the instructions and on the product to make sure the product is suitable for your application. 3. After installation is complete, check out the product operation as provided in these instructions. Wiring WARNING Electrical Shock Hazard. Can cause severe injury, death, or equipment damage. 1. Disconnect the power supply before beginning installation to prevent electrical shock and equipment damage. More than one power supply disconnect can be involved. M35390 Fig. 4. Installing the Base Module on DIN Rail. 1032-00005—01 2. Wiring must comply with all applicable codes, ordinances and regulations. See Table 1, Table 3, and “Recommended Grounding Practices” on page 13 for connections and terminals. For DIP switch settings, see “DIP Switches” on page 15. Note: MS/TP must be wired in a straight line without spurs—no star wiring. Status Main Power INTERNAL SD CARD REMOVEABLE SD CARD USB ETHERNET INPUT POWER L1 L2(N) DIP SWITCHES OK Menu INTERNAL CLOCK BATTERY BACnet AND PROGRAMMABLE POWER SUPPLY ALARM A BG M35391 Fig. 5. Base Module inputs and terminals. SLATE™ BASE MODULE R8001A1001 11 3. Wiring must comply with NEC Class 1 (Line Voltage) wiring. 4. The R8001A1001 should not interfere with the proper safety operation of the controls, limits, and interlocks it is monitoring. After installation, check each control, limit, and interlock to ensure that it is operating properly. DO NOT PLACE JUMPER WIRES ACROSS THE INSTALLATION CONTROLS, LIMITS, AND INTERLOCKS. Application Recommended Wire Size Recommended Part Numbers Line voltage terminals 14, 16, or 18 AWG copper conductor, 600 volt insulation, moistureresistant wire. TTW60C, THW75C, THHN90C Communication linesa 22 AWG two-wire twisted pair with ground, or five-wire. Belden 8723 shielded cable or equivalent. Other terminals 18 AWG wire insulated for voltages and temperatures for given application. TTW60C, THW75C, THHN90C BACnet MS/TP connections must be wired in daisy chain configuration, 1(a)-1(a), 2(b)-2(b), 3(c)-3(c). The order of interconnection of all the devices is not important. Be aware that the termination DIP switch (number 3) must be used if the SLATE system is at the end of connections over 100 feet. a Table 3. Recommended Wire Sizes and Part Numbers. 1232-00005—01 Recommended Grounding Practices Use an Earth ground or a signal ground as described below. Earth ground (Base, Rectification Flame Amp Module, other modules optional) 1. Use to provide a connection between the base and the control panel of the equipment. Earth ground must be capable of conducting enough current to blow the breaker in the event of an internal short circuit. 2. Use wide straps or brackets to provide minimum length, maximum surface area ground conductors. If a leadwire is required, use 14 AWG copper wire. 3. Make sure that mechanically tightened joints along the ground path are free of nonconductive coatings and protected against corrosion on mating surfaces. Signal ground Note the 18V system ground is not electrically connected to earth ground. Follow local codes and appliance recommendations to determine if this should be connected to earth ground. Recommended wire routing of leadwires • Do not run high voltage ignition transformer wires in the same conduit with the flame detector or data lines. • Do not route flame detector or data lines in conduit with line voltage circuits. • Enclose flame detector leadwires without armor cable in metal cable or conduit. • Follow directions in flame detector instructions. Be sure loads do not exceed the terminal ratings. Refer to the labels or terminal ratings in Table 1. The SLATE system must be mounted in an electrical enclosure. When mounting in an electrical enclosure, provide adequate clearance for servicing, installation and removal of SLATE modules. SLATE™ BASE MODULE R8001A1001 13 IMPORTANT 1.This equipment generates, uses and can radiate radio frequency energy and, if not installed and used in accordance with these instructions, may cause interference for radio communications. It has been tested and found to comply with the limits of a Class A computing device of part 15 of FCC rules, which are designed to provide reasonable protection against such interference when operated in a commercial environment. Operation of this equipment in a residential area may cause interference; in which case, the user, at their own expense, may be required to take whatever measures are required to correct this interference. 2.This digital apparatus does not exceed the Class A limits for radio noise, set out in the Radio Interference Regulations of the Canadian Department of Communications. 3.For straight gas burner applications, the oil limit and interlock inputs DO NOT need to be jumpered. 4.For straight oil burner applications, the gas limit and interlock inputs DO NOT need to be jumpered. 5.For combination gas-oil burner applications, a double pole, double throw (dpdt) fuel select switch is required. 6.Cable shield must be terminated to ground at both ends. If shielded cable is NOT used, use three-wire twisted cable. WARNING Electrical Shock Hazard. Can cause severe injury, death or equipment damage. Disconnect the power supply from the main disconnect before beginning installation to prevent electrical shock and equipment damage. More than one disconnect can be required. 1432-00005—01 DIP Switches The SLATE Base Module has three DIP switches. DIP switches 1 and 2 should be On only if no other MS/TP device providing bias resistors is connected. DIP switch 3 should be On only if SLATE is the last device in the communication chain. SLATE™ BASE MODULE R8001A1001 15 32-00005-01 For more information and detailed instructions on the SLATE display please refer to the SLATE User Guide document located on our website at http://combustion.honeywell.com/SLATE Automation and Control Solutions Honeywell International Inc. ® U.S. Registered Trademark. 1985 Douglas Drive North © 2014 Honeywell International Inc. Golden Valley, MN 55422 32-00005—01 M.S. 12-14 customer.honeywell.com Printed in U.S.A.