Description Function and application The LS/PD MULTI 3 FL sensor detects the presence of people and measures the intensity of ambient light. The sensor is installed in lamps. LS/PD MULTI 3 FL Construction A The sensor is made up of the following components: B C • Light sensor (A) • Motion sensor (B) • LED (C) • Connection cable (D) • Housing (E) E D Light and motion sensor Fitting instructions Installation Safety instructions The sensor must only be installed and put into operation by a qualified electrician. The applicable safety regulations and accident prevention regulations must be observed. WARNING! Exposed, live cables or damaged housing. Danger of electric shock! • Only work on the sensor when it is de-energized. CAUTION! Destruction of the sensor and other devices through incorrect mounting! • Only use OSRAM control units of the following types: DALI MULTI 3/ DIM MULTI 3, DALI MULTIeco/ MULTIeco, DALI PROFESSIONAL Sensor Coupler. • Do not connect control line with external voltage. • Note the maximum total line length. • Do not route the sensor line together with the power or lamp line. Connecting the sensor Sensor F DALI MULTI 3 G Connect the sensor using the supplied cable or a commercially available 4-pin cable. If the cable is shortened or lengthened, ensure that the wiring is correct. Sensors can be connected in parallel via a Y-branch. For the maximum number of sensors: see the separate control unit manual. F Y-branch G Sensor II 2009 LSPD_Multi3-FL_ma0902en_we1.01.indd OSRAM GmbH Kunden Service Center Customer-Service-Center (CSC) Steinerne Furt 62 86167 Augsburg Germany Tel : +49 (0) 1803 677 - 200 (kostenpflichtig / charges apply) Fax.: +49 (0) 1803 677 - 202 www.osram.com www.osram.de 40083210473428 4008321047342 Continued on the back page! Selecting the installation location Fitting (cont.) H Surveillance cone: entire workplace; not on window surfaces. 80° 80° I Avoid exposure to direct light. K Avoid drafts (e.g. from ventilators or fans). L Installation distance = min. installation height H I K >h h L Appendix Technical data Combined control and supply connection ∅ 20mm 35mm 4-pin modular connection (4p4c) 1: Supply voltage 2: Light measurement value 3: Motion signal 4: Signal ground 21mm 21mm 20mm 12mm 15mm Length 2.1 m Maximum total length of signal line (incl. all connections to the control units) See control unit Insulation Basic insulation as per IEC 664 Dimensions (L x W x H) 35 x 21 x 21 mm Light sensor detection area 20 - 600 lx (measured at sensor), opening angle approx. 90° Motion detection area Conical, opening angle approx. 80° Installation height 2 - 4 m The CE requirements to EN 60928 are fulfilled. The EMC requirements to EN 61547 are fulfilled. Conformity with the relevant EU directives is confirmed by the CE symbol.