Edco TER Series Single Pair Medium Duty Low Voltage Zone/Horn/Strobe/Data The Edco TER surge suppressor directly installs onto electronic circuit wiring terminal screws. This close proximity preserves Edco TER’s response time, clamping level and ground reference by eliminating lead lengths. The Edco TER’s miniature size fits directly inside fire or security panels, CCTV housings and other system electronic enclosures. These features maximize surge suppression performance while reducing hardware and labor costs to install. General Technical Specifications Operating Voltage 40 VDC Clamping Voltage 43 VDC Operating Current 2A Peak Pulse Current (10 x 1000 μs) 043 = 46.5 A Frequency Range 0 to 20 MHz Insertion Loss < 0.1 dB at 20 MHz SPD Technology Silicon Avalanche Diode (SAD) Connection Type Terminal block w/compression lugs Terminals accept up to 12 AWG Operating Temperature Dimensions (in / mm) Weight (oz / kg) -40°C to +85°C 1.3˝ H x 0.4˝ W x 2.0˝ L [33.02 x 10.16 x 50.8 mm] 0.6 oz [0.02 kg] Certifications UL 497B Warranty 5 years Ordering Information MODEL TER-043 Features ■■ Fits Euro style and barrier strip terminals ■■ Automatic recovery ■■ Single pair protection ■■ High energy silicon avalanche technology ■■ UL 497B listed ■■ Operating current > 2 Amps ■■ Compact size: 1.3˝ H x 0.4˝ W x 2.0˝ L [33.02 x 10.16 x 50.8 mm] ■■ 5 year warranty APPLICATIONS 12 VDC, 24 VDC, 25 VAC Systems Zone, Buss, Loop, Data, Receive, Bell, Horn, Strobe, Pan/Tilt & CCTV Installation Instructions 1. Install zone or loop circuit wires (1 pair) at the vacant end of the Edco TER. Torque terminal screws to 3.5 in. lbs. max. 2. Slip the Edco TER’s Rigid Mounting Prongs into the panels designated Zone or Loop terminals and tighten. 3. Using a 16-12 AWG solid wire, attach all Edco TERs via the center ground terminal. Run this wire to your panel’s “single point” AC power ground or building approved ground. Torque terminal screws to 6.0 in. lbs. max. Fits in series with circuit wires at the terminal screws Note: A. Never install data wiring during a lightning storm. B. Disconnect data line before installing the protection module. C. These protectors are intended for indoor use on communication loop circuits which have been isolated from the Public Switch Telephone Network. D. The communication loop circuits shall not be exposed to accidental contact with the electric light or power conductors. The protectors shall be installed per the applicable requirements of the National Electric Code, ANSI/NFPA 70. V DANGER! Only qualified personnel should install or service this system. Electrical safety precautions must be followed when installing or servicing this equipment. To prevent risk of electrical shock, turn off and lock out all power sources to the unit before making electrical connections or servicing. Seulement le personnel qualifié doit installer ou maintenir ce systéme. Des précautions de sécurité en électricité doivent être suivis lors de l’installation ou de la maintenance de cet equipement. Pour eviter tout risque de choc électrique, débranchez et verouiller toutes les sources d’alimentation de cet equipement avant de. Emerson Network Power Contact information www.EmersonNetworkPower.com/Surge Surge Protection 100 Emerson Parkway Binghamton, NY 13905 T: (607) 721-8840 T: (800) 288-6169 F: (607) 722-8713 E: [email protected] IO-50120 5/14 Rev. 5 Printed in USA Emerson Network Power, the Emerson Network Power logo and Edco are trademarks and service marks of Emerson Electric Co. ©2014 Emerson Electric Co. While every precaution has been taken to ensure accuracy and completeness herein, Emerson Network Power Surge Protection assumes no responsibility, and disclaims all liability, for damages resulting from use of this information or for any errors or omissions. Specifications are subject to change without notice.